Subject: FW: Projekti kooskõlastamine. T-29 Märjamaa uue Kaalumaja ristmiku valgustuse madalpingel liitumine 4 Tallinn-Pärnu-Ikla tee. LC4410
From: Elliko Kõiv <[email-masked]>
To: "MNT Teed" <[email-masked]>
Date: Tue, 13 Jan 2026 14:46:59 +0200

Tere

Edastan.

Parimate soovidega

Elliko Kõiv

Tehnovõrkude koordinaator

Planeerimise osakond

Tehnovõrkude üksus

Tel: 57 848 581

E-post: [email-masked] <mailto:[email-masked]>

www.transpordiamet.ee <http://www.transpordiamet.ee/>

Valge 4 / 11413 Tallinn / Transpordiamet

From: Egle Ninep-Kaselt <[email-masked]>
Sent: Tuesday, January 13, 2026 2:31 PM
To: Elliko Kõiv <[email-masked]>
Subject: Vs: Projekti kooskõlastamine. T-29 Märjamaa uue Kaalumaja ristmiku 
valgustuse madalpingel liitumine 4 Tallinn-Pärnu-Ikla tee. LC4410

Tsau,

Ilusat seda aastat sulle ja perele! 😊

Edastan muudatusega projekti.

Parimate soovidega,

Egle Ninep-Kaselt

Projekteerija

Enersense AS

Mobiil: +372 5597 1898

E-mail:  <mailto:[email-masked]> [email-masked]

Aadress: Mõigu 3 10112 Tallinn

 <http://www.enersense.ee/> www.enersense.ee

 <https://www.linkedin.com/company/enersense-estonia/> 
<https://twitter.com/EnersenseAs> 
<https://www.facebook.com/enersenseestonia> 
<https://www.instagram.com/enersenseestonia/>

This e-mail and any attachments hereto are confidential and intended only 
for a specific individual and purpose. It may contain information which is 
privileged or otherwise protected against unauthorized disclosure or 
communication. If you are not the intended recipient, please notify 
(telephone or e-mail) the sender immediately and delete this message and any 
attachments from your system without producing, distributing or retaining 
copies thereof or disclosing its contents to any other person. Thank you.

Saatja: Elliko Kõiv <[email-masked] 
<mailto:[email-masked]> >
Saatmisaeg: Monday, December 29, 2025 11:03 AM
Adressaat: Egle Ninep-Kaselt <[email-masked] 
<mailto:[email-masked]> >
Teema: RE: Projekti kooskõlastamine. T-29 Märjamaa uue Kaalumaja ristmiku 
valgustuse madalpingel liitumine 4 Tallinn-Pärnu-Ikla tee. LC4410

Hei

Ilmnesid projekti kooskõlastamist takistavad asjaolud, palun vaata üle ja 
korrigeeri 😊

1.	Olen väljastanud 08.12.2025 kirjaga nr 7.1-2/25/20680-2 
„Projekteerimistingimuste taotluse nr 2511002/16232 kooskõlastamine 
märkustega (menetlus nr 520082)“ PT kooskõlastuse.  PT punkt 3, palun võta 
projektid oma töös alla.

Ühtlasi on Laur 18.12.2025 kirjaga nr 7.1-2/25/17727-6 kooskõlastanud 
„Ehitusloa eelnõu nr 2511271/24759 (menetlus nr 515956) kooskõlastamine 
märkustega“ sademeveetorustiku (EHR kood 221495126), tänavavalgustuse (EHR 
kood 221495130), 0,4 kV elektrikaabelliini (EHR kood 221495143), keskpinge 
elektrikaabelliini (EHR kood 221495147), tee (EHR kood 221495151), 
kergliiklustee (EHR kood 221495153) ehitamiseks. Ehitusloa aluseks on 
„Orgita-Päädeva tee nr 5040060 rekonstrueerimise eelprojekt“ 
(peaprojekteerija Selektor Projekt OÜ, töö nr P25004). See on viimane 
versioon, palun võta see alla.

2.	Sisukorras veateade:

3.	Kuna olemasolev reservtoru jääb osaliselt perspektiivse JJT katte alla, 
siis mis on olemasoleva reservtoru sügavus, on Sul teostusjoonis? Sh hetkel 
on segane, kuhu Sa oled kavandanud 750N kaitsetoru. Jooniselt tundub, et 
kogu trassilõigu ulatuses kasutad olemasolevat 450N reservtoru? Tarbija 
kaitsetoru palun kavanda 750N, sh riigiteemaal 750N

Projektis MA17446 on ettenähtud ELV kaabel  likvideeritavana:

Palun vaata lahendus üle ja esita mulle otse e-mailile.

Head vana aasta lõppu

Elliko

From: Egle Ninep-Kaselt <[email-masked] 
<mailto:[email-masked]> >
Sent: Monday, December 22, 2025 9:14 PM
To: [email-masked] <mailto:[email-masked]> ; Andrus 
Tull <[email-masked] <mailto:[email-masked]> >
Subject: Projekti kooskõlastamine. T-29 Märjamaa uue Kaalumaja ristmiku 
valgustuse madalpingel liitumine 4 Tallinn-Pärnu-Ikla tee. LC4410

Tere,

Edastan manuses kooskõlastamiseks T-29 Kaalumaja ristmiku valgustuse 
madalpingel liitumisprojekti.

Parimate soovidega,

Egle Ninep-Kaselt

Projekteerija

Enersense AS

Mobiil: +372 5597 1898

E-mail:  <mailto:[email-masked]> [email-masked]

Aadress: Mõigu 3 10112 Tallinn

 <http://www.enersense.ee/> www.enersense.ee

 <https://www.linkedin.com/company/enersense-estonia/> 
<https://twitter.com/EnersenseAs> 
<https://www.facebook.com/enersenseestonia> 
<https://www.instagram.com/enersenseestonia/>

This e-mail and any attachments hereto are confidential and intended only 
for a specific individual and purpose. It may contain information which is 
privileged or otherwise protected against unauthorized disclosure or 
communication. If you are not the intended recipient, please notify 
(telephone or e-mail) the sender immediately and delete this message and any 
attachments from your system without producing, distributing or retaining 
copies thereof or disclosing its contents to any other person. Thank you.

This e-mail and any attachments hereto are confidential and intended only 
for a specific individual and purpose. It may contain information which is 
privileged or otherwise protected against unauthorized disclosure or 
communication. If you are not the intended recipient, please notify 
(telephone or e-mail) the sender immediately and delete this message and any 
attachments from your system without producing, distributing or retaining 
copies thereof or disclosing its contents to any other person. Thank you.

This e-mail and any attachments hereto are confidential and intended only 
for a specific individual and purpose. It may contain information which is 
privileged or otherwise protected against unauthorized disclosure or 
communication. If you are not the intended recipient, please notify 
(telephone or e-mail) the sender immediately and delete this message and any 
attachments from your system without producing, distributing or retaining 
copies thereof or disclosing its contents to any other person. Thank you.